North American server installations are uniquely inefficient because of multiple circuits, use of floor space and weight, and more. A new approach to power distribution for high-density server installations saves floor space, simplifies power cabling, saves capital cost, reduces weight, and increases electrical efficiency. Learn more about how this distribution architecture can provide you with numerous benefits.
line) Elimination of the PDU transformers A transformer that is used to change 277/480 V to 230/400 V at the output of the UPS. These items are explained in more detail in the following sections. Three-phase branch power distribution '' 230V (line to neutral) instead of 208V (line to line) While the proposed power distribution method sounds like a minor change, it actually creates a very large impact on the power distribution system. First, the typical North American three-phase branch power distribution